Gauge Glass Instructional Video
Simple sight glasses may be just a plastic or glass tube connected to the bottom of the tank at one end and the top of the tank at the other. The level of liquid in the sight glass will be the same as the level of liquid in the tank. Today, however, sophisticated float switches have replaced sight glasses in many such applications.
If the liquid is hazardous or under pressure, more sophisticated arrangements must be made. In the case of a boiler, the pressure of the water below and the steam above is equal, so any change in the water level will be seen in the gauge. The transparent tube (the “glass” itself) may be mostly enclosed within a metal or toughened glass shroud to prevent it from being damaged through scratching or impact and offering protection to the operators in the case of breakage. This usually has a patterned backplate to make the magnifying effect of the water in the tube more obvious and so allow for easier reading. In some locomotives where the boiler operated at very high pressures, the tube itself would be made of metal-reinforced toughened glass.It is important to keep the water at the specified level, otherwise the top of the firebox will be exposed, creating an overheat hazard and causing damage and possibly catastrophic failure.
To check that the device is offering a correct reading and the connecting pipes to the boiler are not blocked by scale, the water level needs to be “bobbed” by quickly opening the taps in turn and allowing a brief spurt of water through the drain cock.